Since 2007, HVAC Warehouse is your best choice for repair, installation, and service in homes and buildings just like yours in the Virginia Beach area. We take special pride in the craftsmen we train and employ--a fact you'll see in their reviews below. Its also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that HVAC Warehouse stands behind the work we do as well as comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC, Plumbing, & Furnace Repair in Chesapeake, VA. Call us today at (757) 962-5047!
Appreciate their willingness to come and make it right.
Service Rep was knowledgeable about our problem and got the toilet reseated/resealed to fix the leakage quickly.
HVAC Warehouse responded very quickly to my initial request for service. Their technician kept me informed during the diagnosis and as he repaired the problem. The service was excellent; the price was very fair and the customer service provided by Kim was outstanding. I recommend them highly!!
Tech very friendly. Showed finished work to ensure I was satisfied.
System working per design at this time.
System is working per design at this time.
Preformed Preventative Maintenance and everything is working per design at this time.
System is back up and running per design.
System is operating properly, no found issues at this time.
Preformed Preventative Maintenance, everything is working properly at this time and there were no found issues.
Performed preventative maintenance on 3 systems on 5/16/17
Inspection of HVAC system
A/C not working properly.
HVAC system install
Repaired leaky kitchen faucet Installed new toilet hardware, new flange, wax ring and toilet bolts.
No Heat: Replaced furnace
Completed preventative maintenance on 2 systems. Systems operating per design
Preventative Maintenance on 2 systems. Completed; all working as per design
Thermostat wire was in bad position; re located wire and fixed issue
Duct cleaned and system fogged with Biofresh to kill present mold/mildew and prevent from further contamination.
Duct cleaning complete. Seal ducting system, clean duct, fog system w/micro-bio spray and replaced filters.
Completed Rinnai Flush and inspection